Scalebreak® quickly removes deposits like lime, scale and rust that otherwise drastically reduce efficiency, increase expenses and damage to vital components.
The third in our series, Cleaning With ScaleBreak®, we are outlining the steps for cleaning evaporative condensers & fluid coolers with ScaleBreak.
When cleaning evaporative condensers or fluid coolers you will first need to visit our calculation tool at www.goodway.com/resources/calculators#!/condenser so you know the proper amount of ScaleBreak needed and how long to perform the circulation. The information in the calculation tool allows you to adjust the amount based on the thickness of scale specific to your system.
- Turn off all water treatment chemicals, pH & conductivity meters. Once the ScaleBreak is added to the basin, it will give false readings to these devices and in turn, they will try to make corrections to the system. You do not want a blow-down of the system initiated where the ScaleBreak will be needlessly purged out. It is equally important to also shut off or disconnect any non-chemical systems, especially alternating high-frequency electric types as leaving this technology on can cause unintended damage to the unit during a cleaning.
- Close the make-up water valve to the basin.
- If possible lower the water volume of the basin but be cautious that you avoid cavitation of the pump. This action will minimize the dilution level of your ScaleBreak once in the system and allow it to dissolve the scale deposits faster.
- If the basin contains loose scale or debris, it is a good practice to remove it prior to a descaling. This can be accommodated by utilizing our Cooling Tower Vacuum (CTV) so the ScaleBreak is not needlessly wasted on these deposits.
- If possible, turn off the fan during the duration of your cleaning. It is possible that the foam generated as a result of the ScaleBreak dissolving the scale could be sucked up and blown out the top.
- Slowly start to add the prescribed amount of ScaleBreak to the water in the basin, preferably on the opposite side of the pump suction. This action will allow the ScaleBreak to dilute first with the water. Please note: do not pour ScaleBreak onto the hot deck, only add it in the basin with the water.
- The foaming reaction is a natural occurrence when ScaleBreak is dissolving the scale deposits in the system.
- If you have a heavily scaled unit, add 25% of the recommended amount, wait 20 minutes and add the next 25%. Follow this procedure until all the ScaleBreak is in the system. If you encounter a substantial foaming reaction, you can wait 30-45 minutes or until the foaming subsides to controllable amounts before adding more product. Defoamers are not recommended as the foaming can be controlled by minimizing the overall concentration.
- During your ScaleBreak cleaning, you will want to make sure your solution remains active. For this step, please follow our “Testing ScaleBreak’s Effectiveness” procedure.
- Should all your ScaleBreak become neutralized during the cleaning process, this is an indication you had more scale in the system than anticipated. Additional product will be required to complete your cleaning. What happens is every descaling product has a saturation point, once it dissolves its maximum ability, it becomes neutralized.
- Upon completion of the cleaning, shut off the pump and check the pH of the cleaning solution in your basin. Though ScaleBreak is a biodegradable solution, most facilities need to conform to pH discharge limits. ScaleBreak Neutralizer can be utilized to safely elevate your pH to meet your discharge limit so it can be flushed to the drain. Please follow the instructions for this process in the ScaleBreak Neutralizer information sheet.
- Once you know your unit is ready to be flushed and your pH value is met, you can turn on your make-up water, open the drain valve and initiate a blowdown of the unit. This will flush out the cleaning solution and suspended solids.
- If after a cleaning some heavy debris were released and are now in the bottom of the basin, you can utilize our Cooling Tower Vacuum (CTV) to vacuum this debris out.
- Once the system has been flushed, you can reestablish pH & conductivity meters, turn on non-chemical treatment systems or water treatment chemical feeds.
- Follow all local regulations for discharge.
- Follow all plant personal protective equipment guidelines as determined by your health & safety team.
- ScaleBreak formulas have very minimal corrosion rates, however, the application of ScaleBreak may reveal pre-existing under-deposit corrosion (UD). This type of corrosion can present itself in the form of pitting, pinholes or similar types of damage.
Please contact Goodway Technologies with any questions.